Log in if you have an account
By creating an account with our store, you will be able to move through the checkout process faster, store multiple addresses, view and track your orders in your account, and more.Create an account
Warmup Loose Wire System - 120V 240ft
Product Type: Loose Wire Heating System
Model Number: NADWS-120-840
Product Voltage: 120 V
Product Length: 240 ft
Warmup Loose Cable systems are designed using a 1/8" (2mm), ultra-thin, dual-core floor heating cable that can be installed in a matter of hours without raising floor levels. The loose cable system can be used under carpet, vinyl, wood or any ceramic or natural stone floor tile. Simply position the floor heating cable on the subfloor, lay your flooring and say goodbye to cold feet for good!
You do not need specialist skills to lay the heating element but you must use a certified electrician for the wiring.
Features and Benefits
Ultra-thin dual-core heating element won't raise floor levels
Toughest and thinnest wire you can buy: 1/8" (2mm), multi-stand core, double insulated using advanced fluoropolymers
Tested and approved heating element meets the highest safety standards
Quick installation - Single connection lead for fewer steps
Available in both 120V and 240V
Warmup® 30-year transferable warranty
Warmup® SafetyNet™ installation guarantee
Product Code: NADWS-120-840
Coverage at 14W/ft² (3" Spacing) 60
Coverage at 11W/ft² (4" Spacing) 80
Cable Length (ft) 240
Loose Wire Technical Specifications
Heater Construction Dual Core Earth Screened Cable (50Hz)
Operating Voltage 120-240V (50Hz)
Cable Thickness 1/8" (2mm)
Inner Insulation Advanced Fluoropolymers
Outer Insulation Advanced Fluoropolymers
Average Wattage Output 14 W/sq ft
Cold Tail Length 9ft (3m)
How to Install
Make sure that your sub-floor is clean and dry. Lay down the provided fixing strips on two opposite sides of the room. It may be necessary to install strips in the middle of the room to secure the cables. Secure the fixing strips with glue, screws, nails or staples.
The cable can be secured around the strips at the desired spacing (between 3 or 4 inches) so that all the cable is evenly spaced. Remember, you cannot cut or shorten the cable at any stage.
Secure factory joint to the subfloor and route the lead wire through the conduit into the thermostat box. In a separate conduit, bring the sensor down to the floor and position in the heated area. Finally, test the heating wires with an Ohmmeter for continuity and note the resistance on the Warranty Registration form.
Apply thinset or self-leveling cement over the cables, about 1/4” thick. Work cautiously when using a metal trowel to avoid cable damage or movement. Let the scratch coat dry fully (a few hours to overnight) before flooring installation.
0 stars based on 0 reviews
Add your review
Review Washers w/o tabs for 1/4” WIB Installation. Sold in box of 100 ct.